40MVC / 38MVC. 40MVQ / 38MVQ. Service Manual. HighWall Duct Free Split System. Sizes To TABLE OF CONTENTS. PAGE. SAFETY. View and Download Carrier 40MVC product data online. High-Wall Duct Free Split System. 40MVC Air Conditioner pdf manual download. Also for: 38mvc. Manuals and User Guides for CARRIER 40MVC. We have 5 CARRIER 40MVC manuals available for free PDF download: Service Manual, Product Data.
|Published (Last):||1 February 2008|
|PDF File Size:||3.30 Mb|
|ePub File Size:||11.74 Mb|
|Price:||Free* [*Free Regsitration Required]|
Table of Contents Add to my manuals Add.
CARRIER 40MVC INSTALLATION INSTRUCTIONS MANUAL Pdf Download.
All connections between indoor and outdoor units must be as shown. Safety Considerations Installing, starting up, and servicing air- -conditioning equipment These instructions cover the installation, start- -up and servicing of can be hazardous due to system pressures, electrical components, 38MVC,MVQ outdoor and 40MVC, MVQ indoor units duct free and equipment location roofs, elevated structures, etc.
Don’t have an account?
Parts List Aa Aa Fig. Got it, continue to print. Comments to this Manuals Your Name. Enter text from picture: Page of 35 Go. This manual also for: The ideal compliment to your ducted system when it is impractical.
Installing, starting up, and servicing air- -conditioning equipment These instructions cover the installation, start- -up and servicing of can be hazardous due to system pressures, electrical components, 40mmvc outdoor and 40MVC, MVQ indoor units duct free and equipment location roofs, elevated structures, etc. Contact your Carrier accessory condensate 40vmc. Enter text from picture: If possible, display LEDs on both the indoor and outdoor units. Carefully remove the mounting plate, which is attached to the back of the indoor unit.
By pressing ‘print’ button 40,vc will print only current page.
The fan coil is mounted on the wall, near the ceiling. Outdoor Unit Installation If the installation location may be exposed to strong winduse a ends until all the connections are made.
Carrier 40MVC User Manual
ccarrier Don’t have an account? Page 14 Catalog No: Carrifr print the manual completely, please, download it. These compact indoor fan coil units take up very little space in the. Run interconnecting cable through hole in wall outside to inside. Do not use thermostat wire for any connection between indoor and outdoor units. All minimum spacings shown in Fig. Lift indoor unit into position and route piping and drain Do not form a rise.
Got it, continue to print. The outdoor always check the diagnostic codes displayed on the indoor unit diagnostic display is an LED on the outdoor unit board and is first.
Carrier 40MVC Manuals
High-wall ductless split system sizes to 40 pages. By pressing ‘print’ button you will print only current page. The mounting plate should be located horizontally and level Indoor Unit on the wall.
Page of 14 Go. Don’t show me this message again.
If the installation location may be exposed to strong winduse a ends until all the connections are made. The deep vacuum method is the most positive way of assuring a system is free of air and Failure to follow this caution may result in equipment liquid water.
Application Data If unit is exposed to strong winds it is drainage cannot be provided, unit should be equipped with recommended that a wind baffle be used. Refrigerant Lines -in mm should be buried.
Comments to this Manuals Your Name. Conceal the tubing where possible. Failure to follow this caution may result in equipment 4. Run power wiring from main box to disconnect per NEC and local codes. Check with your Carrier representative carfier obtain Bend tubing with bending tools to avoid kinks and flat spots. Add- -ons to current space an office or family room. This manual also for: Remove field wiring cover from unit by loosening screws.